The Advanced Energy Design Guide for Grocery Stores (AEDG-Grocery) is intended to provide a simple approach for contractors, designers, and owners to achieve 50% savings in grocery stores and other like retail that has refrigeration systems. Application of the recommendations in the Guide should result in grocery stores with 50% energy savings when compared to those same stores designed to the minimum requirements of ANSI/ASHRAE/IESNA Standard 90.1-2004. Energy Standard for Buildings Except Low-Rise Residential Buildings.
Advanced SearchYour search resulted in 3 resources
In 2011, the U.S. Department of Energy’s Building Technology Office (DOE’s BTO), with help from the Better Buildings Alliance (BBA) members, developed a specification (RTU Challenge) for high performance rooftop air-conditioning units with capacity ranges between 10 and 20 tons (DOE 2013). In April 2013, Carrier’s 10-ton WeatherExpert unit model was recognized by DOE to have met the RTU Challenge specifications. Carrier also committed to have its entire line of WeatherExpert models for commercial buildings compliant with integrated energy efficiency ratio (IEER) meeting the RTU Challenge requirement. This report documents the development of part-load performance curves and their use with the EnergyPlus simulation tool to estimate the potential savings from the use of WeatherExpert units compared to other standard options.
A detailed EnergyPlus model was developed for a prototypical big-box retail store. The model used the performance curves from the new model along with detailed energy management control code to estimate the energy consumption of the prototypical big-box retail store in three locations. The energy consumption by the big-box store was then compared to a store that used three different reference units. The first reference unit (Reference 1) represents existing rooftop units (RTUs) in the field, so it can be considered the baseline to estimate potential energy savings from other RTU replacement options. The second reference unit (Reference 2) represents RTUs in the market that just meet the current (2015) Federal regulations for commercial equipment standards, so it can be used as the baseline to estimate the potential for energy savings from WeatherExpert units in comparison with new RTUs that meet the minimum efficiency requirements. The third reference unit (Reference 3) represents units that meet ASHRAE 90.1-2010 requirements. For RTUs with cooling capacity greater than 11,000 Btu/h, ASHRAE 90.1-2010 (ASHRAE 2010) requires two-speed fan control or variable-speed fan control.
The following conclusion can be drawn about the comparison of energy cost for WeatherExpert unit compared to the three reference units:
• Using Reference 1 as the baseline, WeatherExpert units result in about 45% lower heating, ventilation and air conditioning (HVAC) energy cost in Houston, 55% lower cost in Los Angeles, and 35% lower cost in Chicago. The percentage savings of electricity cost is more than 50% for all three locations.
• Using Reference 2 as the baseline, WeatherExpert units result in about 39% lower HVAC energy cost in Houston, 52% lower cost in Los Angeles, and 32% lower cost in Chicago. The percentage savings of electricity cost is 44%, 55%, and 57%, respectively for the three locations.
• Using Reference 3 as the baseline, WeatherExpert units result in about 25% lower HVAC energy cost in Houston, 35% lower cost in Los Angeles, and 18% lower cost in Chicago. The percentage savings of electricity cost is 29%, 38%, and 37%, respectively.
Based on the simulation results, the WeatherExpert RTU Challenge unit, if widely adopted, could lead to significant energy, cost and emission reductions. Because the cost of these units was not available and because the costs would be specific to a given installation, no attempt was made to estimate the potential payback periods associated with any of the three reference scenarios. However, if the incremental cost relative to any of the three reference cases is known, one can easily estimate a simple payback period.
Find the presentation for the June 3, 2015 webinar on the 50% Advanced Energy Design Guide for Grocery Stores below.
The guide shows practical ways for grocery stores to achieve a 50% energy savings over ASHRAE 90.1-2004 and exceeds the requirements of 90.1-2013. Intended for grocery stores owners and designers, the guide includes specialty sections for refrigeration and food service found, not only in grocery stores but in convenience stores and food service establishments as well.
Speakers highlighted the guide, providing practical how-to tips to achieve the 50% savings level. The guide also helps those who build or design retail stores that may include refrigeration.
Below are the speakers from the webinar.
-Michael Lane, Puget Sound Energy
-Merle McBride, Owens Corning
-Caleb Nelson, CTA Group
-Paul Torcellini, National Renewable Energy Laboratory.