Case study describing how adidas implemented a best practice of a planned replacement program for its rooftop units (RTUs), which resulted in significant cost and energy savings. The case study outlines the planning process, implementation, results, and the future plans of their RTU replacement program.
Advanced SearchYour search resulted in 19 resources
This document provides facility managers and building owners with an introduction to measurement and verification (M&V) methods to estimate energy and cost savings of rooftop units replacement or retrofit projects. The M&V methods presented here are helpful in estimating paybacks to justify future projects.
This checklist will assist facility managers and building owners evaluate the capabilities of HVAC companies and the proposals they submit for installation of new HVAC equipment. The questions on the checklist will help owners and managers understand the requirements contained within the ACCA HVAC quality installation Standard 5.
This case study details the very successful Walgreens proactive RTU replacement program that has resulted in 50% efficiency improvements. The streamlined process allows Walgreens to reduce installed cooling capacity, increase RTU efficiency, provide improved service, and reduce overall costs compared to emergency replacements.
JCPenney saved over 47 million kWh and $5 million with variable frequency drive retrofits of rooftop units across 131 stores. The case study describes the decision process and results of this successful program.
In FY14, BTO funded PNNL to develop and integrate AFDD methods for both air-side and refrigerant-side fault detection and diagnostics with one of the leading advanced RTU controllers sold in the market today. The work also includes testing and validating the integrated solution in the field. If the results from the field demonstrations show reliable fault diagnostics, it will encourage utilities to provide incentives to pursue the integrated technology because it makes the retrofit controller more cost effective and could make market adoption of the retrofit controller even more attractive to building owners.
Seven AFDD algorithms were developed, deployed and tested on the RTU controller for detecting and diagnosing faults with RTU economizer and ventilation operations using sensors that are commonly installed for advanced control purposes.
"This paper discusses the evidence regarding daylighting and student performance and development, and presents four case studies of schools that have cost effectively implemented daylighting into their buildings."
This study expands and validates previous research by Heschong Mahone Group that found a statistical correlation between the amount of daylight in elementary school classrooms and student performance. The researchers reanalyzed student performance data from two school districts to answer questions raised by the previous study. The results are consistent with the original findings and affirm that daylight has a positive and highly significant association with improved student performance.
A report with case studies on 15 Zero Energy schools in the U.S., prepared to help Baltimore City Schools in its building planning.
A detailed two page case study on the Zero Energy Ready Turkey Foot Middle School.
"Turkey Foot is revolutionizing the way kids learn, all within a new building that uses half the energy of the previous school despite being twice the size. Turkey Foot leveraged the practices and experience on other high performance goals in the District."