A recast of a presentation done for the Fairfax Chapter of Association of Energy Engineers in November of 2013. Presentation focuses on the the Advanced Energy Design Guides published by ASHRAE with association of AIA, USGBC, and IES with funding and technical support from DOE, NREL, and PNNL. In addition, the DOE Advanced Retrofit Guides are also discussed. Both sets of guides are available for download from this resource database.
Advanced SearchYour search resulted in 10 resources
This checklist will assist facility managers and building owners evaluate the capabilities of HVAC companies and the proposals they submit for installation of new HVAC equipment. The questions on the checklist will help owners and managers understand the requirements contained within the ACCA HVAC quality installation Standard 5.
In 2011, the U.S. Department of Energy’s Building Technology Office (DOE’s BTO), with help from the Better Buildings Alliance (BBA) members, developed a specification (RTU Challenge) for high performance rooftop air-conditioning units with capacity ranges between 10 and 20 tons (DOE 2013). In April 2013, Carrier’s 10-ton WeatherExpert unit model was recognized by DOE to have met the RTU Challenge specifications. Carrier also committed to have its entire line of WeatherExpert models for commercial buildings compliant with integrated energy efficiency ratio (IEER) meeting the RTU Challenge requirement. This report documents the development of part-load performance curves and their use with the EnergyPlus simulation tool to estimate the potential savings from the use of WeatherExpert units compared to other standard options.
A detailed EnergyPlus model was developed for a prototypical big-box retail store. The model used the performance curves from the new model along with detailed energy management control code to estimate the energy consumption of the prototypical big-box retail store in three locations. The energy consumption by the big-box store was then compared to a store that used three different reference units. The first reference unit (Reference 1) represents existing rooftop units (RTUs) in the field, so it can be considered the baseline to estimate potential energy savings from other RTU replacement options. The second reference unit (Reference 2) represents RTUs in the market that just meet the current (2015) Federal regulations for commercial equipment standards, so it can be used as the baseline to estimate the potential for energy savings from WeatherExpert units in comparison with new RTUs that meet the minimum efficiency requirements. The third reference unit (Reference 3) represents units that meet ASHRAE 90.1-2010 requirements. For RTUs with cooling capacity greater than 11,000 Btu/h, ASHRAE 90.1-2010 (ASHRAE 2010) requires two-speed fan control or variable-speed fan control.
The following conclusion can be drawn about the comparison of energy cost for WeatherExpert unit compared to the three reference units:
• Using Reference 1 as the baseline, WeatherExpert units result in about 45% lower heating, ventilation and air conditioning (HVAC) energy cost in Houston, 55% lower cost in Los Angeles, and 35% lower cost in Chicago. The percentage savings of electricity cost is more than 50% for all three locations.
• Using Reference 2 as the baseline, WeatherExpert units result in about 39% lower HVAC energy cost in Houston, 52% lower cost in Los Angeles, and 32% lower cost in Chicago. The percentage savings of electricity cost is 44%, 55%, and 57%, respectively for the three locations.
• Using Reference 3 as the baseline, WeatherExpert units result in about 25% lower HVAC energy cost in Houston, 35% lower cost in Los Angeles, and 18% lower cost in Chicago. The percentage savings of electricity cost is 29%, 38%, and 37%, respectively.
Based on the simulation results, the WeatherExpert RTU Challenge unit, if widely adopted, could lead to significant energy, cost and emission reductions. Because the cost of these units was not available and because the costs would be specific to a given installation, no attempt was made to estimate the potential payback periods associated with any of the three reference scenarios. However, if the incremental cost relative to any of the three reference cases is known, one can easily estimate a simple payback period.
A net zero-energy community (ZEC) is one that has greatly reduced energy needs through efficiency gains such that the balance of energy for vehicles, thermal, and electrical energy within the community is met by renewable energy. Past work resulted in a common zero-energy building (ZEB) definition system of “zero energy” and a classification system for ZEBs based on the renewable energy sources used by a building. This paper begins with a focus solely on buildings and expands the concept to define a zero-energy community, applying the ZEB hierarchical renewable classification system to the concept of community. A community that offsets all of its energy use from renewables available within the community’s built environment and unusable brownfield sites is at the top of the ZEC classification system at a ZEC of A. (A brownfield site is where the redevelopment or reuse may be complicated by the presence or potential presence of a hazardous substance, pollutant or contaminant.) A community that achieves a ZEC definition primarily through the purchase of new off-site, Renewable Energy Certificates (RECs) is placed at the lowest end of the ZEC classification but is still considered a good achievement.
Power purchase agreement presentation for government buildings under the federal energy management program (FEMP).
Designed as a resource for those who want to develop community solar projects, from community organizers or solar energy advocates to government officials or utility managers. By exploring
the range of incentives and policies while providing examples of operational community solar projects, this guide will help communities to plan and implement successful local energy projects. In addition, by highlighting some of the policy best practices, this guide suggests changes in the regulatory landscape that could significantly boost community solar installations across the country.
Case study on how Fontana Unified School District in southern California used grant money to install 201 high-efficiency Carrier rooftop units (RTUs) in 30 buildings across four schools, resulting in $214,000 saved per year.
Case study on how Arby's Restaurant Group's innovative approach to rooftop unit (RTU) management garnered them $287,000 and 2.9 million kWh in annual savings.
Encouraging commercial building owners to set measurable energy goals before design begins can drive design and contractor teams to develop innovative energy efficiency solutions within conventional building budgets. The successes and lessons learned by a federal building owner's performance-based procurement project formed the basis of an expanded program using utilities as the outreach channel to replicate the approach. The utilities delivered incentive-based offerings to focus building owners on the whole building rather than on individual building components and systems. This 11-page paper documents the core principles, successes and lessons learned from these utility programs in different areas of the country.
Article in the Whole Building Design Guide about the uses and features of metal roofs that meet "cool roof" standards.