Plug and process loads (PPLs) in commercial buildings account for almost 5% of U.S. primary energy consumption. Minimizing these loads is a primary challenge in the design and operation of an energy-efficient building. PPLs are not related to general lighting, heating, ventilation, cooling, and water heating, and typically do not provide comfort to the occupants. They use an increasingly large fraction of the building energy use pie because the number and variety of electrical devices have increased along with building system efficiency. Reducing PPLs is difficult because energy efficiency opportunities and the equipment needed to address PPL energy use in office spaces are poorly understood.
Advanced SearchYour search resulted in 10 resources
This report discusses miscellaneous electrical loads, which are building loads that are not related to general lighting, heating, ventilation, cooling, and water heating, and typically do not provide comfort to the occupants. MELs in commercial buildings account for almost 5% of U.S. primary energy consumption.
In typical computer centers you can feel the energy consumption from racks of servers radiating heat, while icy air blows through the room to cool them. NREL’s fully contained hot and cold aisle data center configuration minimizes this problem. The configuration includes effective air-side economizer cooling with an evaporative boost when needed.
This document highlights the key accomplishments in Green IT of the 17 DOE labs.
Plug and process loads in commercial buildings account for 5% of U.S. primary energy consumption. Minimizing these loads is a primary challenge in the design and operation of an energy-efficient building.
This presentation describes how the designers, owners, and occupants can take advantage of opportunities to reduce plug loads in the Research Support Facility.
This presentation decribes how building an energy-efficient data center can improve a business's bottom line.
The Research Support Facility complex (RSF, RSF II, parking garage, and associated site lighting) was designed to produce more on-site renewable energy than it uses over the course of a typical weather year, when accounted for at the site. To date, the end use performance monitoring and verification suggests that when the RSF complex is fully built out, we will meet the annual energy use goals. Continued performance monitoring and occupant education are required to ensure annual energy use goals will continue to be met.
This presentation highlights the importance of modeling the off-design performance of equipment in data centers as a consequence of their dynamic behavior and describes an experimentally validated tool for modeling the energy use of the data center and cooling infrastructure.
This presentation Session II from the RSF Workshop discusses the performance-based design-build process, which was used to procure and construct the Research Support Facility.