A recast of a presentation done for the Fairfax Chapter of Association of Energy Engineers in November of 2013. Presentation focuses on the the Advanced Energy Design Guides published by ASHRAE with association of AIA, USGBC, and IES with funding and technical support from DOE, NREL, and PNNL. In addition, the DOE Advanced Retrofit Guides are also discussed. Both sets of guides are available for download from this resource database.
Advanced SearchYour search resulted in 17 resources
NorthBay VacaValley Hospital completed lighting retrofits to their 150,000 square foot parking lot and its 225 parking spaces. They did so with help from The California Lighting Technology Center (CLTC) at the University of California, Davis. The project has achieved 65% savings and received a 2014 Lighting Energy Efficiency in Parking (LEEP) Campaign’s award for best use of lighting controls. In addition, the retrofits improved lighting maintenance operations and end-user satisfaction.
The lighting retrofit included replacing roughly 50 induction luminaires with new LED fixtures with embedded lighting controls.
The new LED fixtures were coupled with various kinds of lighting control systems, including a radio frequency (RF) connectivity control system that was installed in dedicated zones with passive- infrared (PIR) and long-range microwave sensors to achieve energy savings. An “ultra-smart” lighting control network was also put in place, giving facility managers the ability to adjust lighting schedules, light levels and time-out settings, monitor the system’s energy use, and receive automated alerts when luminaires require maintenance.
This guide covers each major step in procuring a solar photovoltaic (PV) system:
- Conducting technical and financial studies
- Financing a PV system
- Project execution
- Operations and maintenance
- Assessing benefits
The guide provides information on the basic steps, key considerations, and where to go for more information. It is intended to provide an overview and some level of detail, with pointers to highly detailed information and resources.
"This paper discusses the evidence regarding daylighting and student performance and development, and presents four case studies of schools that have cost effectively implemented daylighting into their buildings."
"Improved lighting efficiency has long been a major strategy to reduce the energy use in buildings. These savings have traditionally come from improved efficiency of lamps and ballasts. Today, deep energy reductions and Zero Net Energy (ZNE) are possible by continually controlling each of these efficient fixtures in response to varying details within the space. This guide provides an overview of luminaire-level lighting control (LLLC). The full LLLC approach provides controllability at each fixture with real-time energy tracking and data collection."
"Zero Net Energy (ZNE) is the future, and in a growing number of places the present, of building design and energy policy. A growing strategy to get to ZNE is to separate the building’s heating/cooling from the ventilation/dehumidification. Design firms and owners are striving to meet heating, ventilation and air-conditioning (HVAC) loads with optimum comfort and minimal energy. Radiant systems can provide heating and cooling through pipes while ventilation and any humidity control requirements are efficiently met by a Dedicated Outdoor Air System (DOAS). This guide provides an overview of Radiant Heating and Cooling + DOAS systems."
How to determine the amount of continuous insulation required by codes, while still retarding water vapor according to climate zone locations
"While ASHRAE 90.1 has been pushing continuous insulation (CI) for the past decade, the building codes are catching on. And now that the U.S. Department of Energy (DoE) has mandated all states to adopt a commercial building energy code that meets or exceeds ASHRAE Standard 90.1-2010, CI specifications are really being cast into the spotlight."
In the cold climate of the upper Midwest, air-source VRF systems have difficulty meeting heating loads when the outdoor temperatures drop below -5ºF. Because of this difficulty during common cold spells, they are either oversized (adding to system cost) or supplemental heat is added (adding to operating cost). Cold temperatures can also cause frost issues around outdoor units, as well as compressor failure. A VRF system served by a water loop—in place of air—does not have these issues, making the technology more practical and effective in cold climates such as the upper Midwest. A water-source VRF system can be connected to a boiler and cooling tower or, for even higher performance, a ground heat exchanger.
This guide primarily applies to facility managers and energy managers of large existing office buildings larger than 100,000 square feet, but also includes considerations for small and medium office buildings. By presenting general project planning guidance as well as financial payback metrics for the most common energy efficiency measures, this guide provides a practical roadmap for effectively planning and implementing performance improvements for existing buildings.