Plug and process loads (PPLs) in commercial buildings account for almost 5% of U.S. primary energy consumption. Minimizing these loads is a primary challenge in the design and operation of an energy-efficient building. PPLs are not related to general lighting, heating, ventilation, cooling, and water heating, and typically do not provide comfort to the occupants. They use an increasingly large fraction of the building energy use pie because the number and variety of electrical devices have increased along with building system efficiency. Reducing PPLs is difficult because energy efficiency opportunities and the equipment needed to address PPL energy use in office spaces are poorly understood.
Advanced SearchYour search resulted in 27 resources
This report discusses miscellaneous electrical loads, which are building loads that are not related to general lighting, heating, ventilation, cooling, and water heating, and typically do not provide comfort to the occupants. MELs in commercial buildings account for almost 5% of U.S. primary energy consumption.
Conventional information technology (IT) equipment and data center spaces can consume more than 100 times the energy of standard office spaces, so the potential for energy savings is huge. You can use this application guide to reduce your equipment energy consumption in any building with a data center, server closets, or other IT equipment (computers, printers, etc.). Some of these strategies are most effective at the beginning of the design process; others can be implemented at any time and be sequenced as part of the normal procurement and replacement schedule.
Plug and process loads in commercial buildings account for 5% of U.S. primary energy consumption. Minimizing these loads is a primary challenge in the design and operation of an energy-efficient building.
This presentation describes how the designers, owners, and occupants can take advantage of opportunities to reduce plug loads in the Research Support Facility.
The Research Support Facility complex (RSF, RSF II, parking garage, and associated site lighting) was designed to produce more on-site renewable energy than it uses over the course of a typical weather year, when accounted for at the site. To date, the end use performance monitoring and verification suggests that when the RSF complex is fully built out, we will meet the annual energy use goals. Continued performance monitoring and occupant education are required to ensure annual energy use goals will continue to be met.
This presentation Session I from the RSF Workshop discusses the unique energy efficiency features and performance of the Research Support Facility.
McGraw Hill Construction Continuing Education Article December 2010 - This article discusses the energy efficiency and cost competitiveness of the Research Support Facility.
This guide provides design teams with best practices for parking structure energy efficiency in the form of goals for each design aspect that affects energy use.
NorthBay VacaValley Hospital completed lighting retrofits to their 150,000 square foot parking lot and its 225 parking spaces. They did so with help from The California Lighting Technology Center (CLTC) at the University of California, Davis. The project has achieved 65% savings and received a 2014 Lighting Energy Efficiency in Parking (LEEP) Campaign’s award for best use of lighting controls. In addition, the retrofits improved lighting maintenance operations and end-user satisfaction.
The lighting retrofit included replacing roughly 50 induction luminaires with new LED fixtures with embedded lighting controls.
The new LED fixtures were coupled with various kinds of lighting control systems, including a radio frequency (RF) connectivity control system that was installed in dedicated zones with passive- infrared (PIR) and long-range microwave sensors to achieve energy savings. An “ultra-smart” lighting control network was also put in place, giving facility managers the ability to adjust lighting schedules, light levels and time-out settings, monitor the system’s energy use, and receive automated alerts when luminaires require maintenance.