This case study describes the National Renewable Energy Laboratory's (NREL) data center as a showcase of energy efficiency. Most of what NREL has done can be replicated by clients; however, two design approaches are climate-dependent: near-full reliance on outside air for cooling, and photovoltaic arrays for power.
Advanced SearchYour search resulted in 14 resources
This publication details the design, implementation strategies, and continuous performance monitoring of NREL's Research Support Facility data center.
This case study details the design and operations of the National Renewable Energy Laboratory (NREL) Research Support Facility data center and its contributions to energy efficiency.
InterContinental Hotels Group (IHG) and its franchise partner B.F. Saul Company Hospitality Group (B.F. Saul Co.) partnered with the Department of Energy (DOE) to develop and implement solutions to retrofit existing buildings to reduce energy consumption by at least 30% versus requirements set by Standard 90.1-2004 of the American Society of Heating, Refrigerating, and Air-Conditioning Engineers (ASHRAE), the American National Standards Institute (ANSI), and the Illuminating Engineering Society of North America (IESNA) as part of DOE’s Commercial Building Partnerships (CBP) Program.
An energy-efficient data center includes targets for its power usage effectiveness (<1.2) and energy resource efficiency (< 0.9). It should be designed with hot isle–cold isle separation, use free cooling (economizer) and evaporative cooling when available, minimize fan energy, and use the most energy-efficient equipment possible.
Bank of America partnered with DOE's Commercial Building Partnerships (CBP) Program to develop and implement solutions to build a new bank branch in Punta Gorda, Florida, with a goal of being at least 50% below ASHRAE Standard 90.1-2004. The branch opened in October 2011 and achieved actual energy savings of 47%.
PNC Financial Services partnered with DOE's Commercial Building Partnerships (CBP) Program to develop and implement solutions to retrofit its existing Singer Island, Florida, branch to reduce energy consumption by at least 30% versus ASHRAE Standard 90.1-2004. Construction was completed in January 2012.
OpenStudio development efforts have been focused on providing Application Programming Interfaces (APIs) where users are able to extend OpenStudio without the need to compile the open source libraries. This paper will discuss the basic purposes and functionalities of the core libraries that have been wrapped with APIs including the Building Model, Results Processing, Advanced Analysis, Uncertainty Quantification, and Data Interoperability through Translators. Several building energy modeling applications have been produced using OpenStudio's API and Software Development Kits (SDK) including the United States Department of Energy's Asset ScoreCalculator, a mobile-based audit tool, an energy design assistance reporting protocol, and a portfolio scale incentive optimization analysis methodology. Each of these software applications will be discussed briefly and will describe how the APIs were leveraged for various uses including high-level modeling, data transformations from detailed building audits, error checking/quality assurance of models, and use of high-performance computing for mass simulations.
Case study describing how adidas implemented a best practice of a planned replacement program for its rooftop units (RTUs), which resulted in significant cost and energy savings. The case study outlines the planning process, implementation, results, and the future plans of their RTU replacement program.
Cooling loads must be dramatically reduced when designing net-zero energy buildings or other highly efficient facilities. Advances in this area have focused primarily on reducing a building’s sensible cooling loads by improving the envelope, integrating properly sized daylighting systems, adding exterior solar shading devices, and reducing internal heat gains. As sensible loads decrease, however, latent loads remain relatively constant, and thus become a greater fraction of the overall cooling requirement in highly efficient building designs, particularly in humid climates. This shift toward latent cooling is a challenge for heating, ventilation, and air-conditioning (HVAC) systems. Traditional systems typically dehumidify by first overcooling air below the dew-point temperature and then reheating it to an appropriate supply temperature, which requires an excessive amount of energy. Another dehumidification strategy incorporates solid desiccant rotors that remove water from air more efficiently; however, these systems are large and increase fan energy consumption due to the increased airside pressure drop of solid desiccant rotors. A third dehumidification strategy involves high flow liquid desiccant systems. These systems require a high maintenance separator to protect the air distribution system from corrosive desiccant droplet carryover and so are more commonly used in industrial applications and rarely in commercial buildings. Both solid desiccant systems and most high-flow liquid desiccant systems (if not internally cooled) add sensible energy which must later be removed to the air stream during dehumidification, through the release of sensible heat during the sorption process.