This report describes the psychrometric bin analysis that was conducted for the ASHRAE recommended and allowable operating environment zones as well as a modified allowable operating environment, discusses control strategies, and presents examples of energy-efficient data centers using alternative cooling strategies.
Advanced SearchYour search resulted in 52 resources
NREL's sustainability vision is to build a laboratory of the future that is committed to sustainability, which is built on a framework of economic viability, environmental health, and public responsibility over the long term through appropriate investment decisions and operating practices.This report shows NREL’s progress in making sustainability an integral part of its corporate culture and providing a global sustainability model
This study analyzes the market needs for building performance evaluation tools. The purpose is to identify existing gaps and provide information for the U.S. Department of Energy (DOE) to use in developing a linked set of tools for optimizing energy performance of commercial buildings over their life cycles.
This report presents a set of 15 best practices for owners, designers, and construction teams to reach high-performance goals and maintain a competitive budget. These best practices are based on the recent experiences of the Research Support Facility owner and design-build team for the Research Support Facility (RSF) on the National Renewable Energy Laboratory’s (NREL) campus in Golden, Colorado, and show that achieving this high performance outcomes requires that all key integrated team members understand their opportunities to control capital costs.
This Technical Support Document describes the process and methodology for the development of the Advanced Energy Design Guide for Large Hospitals: Achieving 50% Energy Savings Toward a Net Zero Energy Building (AEDG-LH) ASHRAE et al. (2011b). The AEDG-LH is intended to provide recommendations for achieving 50% whole-building energy savings in large hospitals over levels achieved by following Standard 90.1-2004. The AEDG-LH was created for a “standard” mid- to large-size hospital, typically at least 100,000 ft², but the strategies apply to all sizes and classifications of new construction hospital buildings. Its primary focus is new construction, but recommendations may be applicable to facilities undergoing total renovation, and in part to many other hospital renovation, addition, remodeling, and modernization projects (including changes to one or more systems in existing buildings).
This report highlights the funding opportunities available to rural communities and small buildings. Most of these communities qualify for USDA programs and these incentives and grants can be used to make rural communities more efficient.
The rooftop unit (RTU) Field Evaluation Checklist is intended to help identify damage, dysfunction, or degradation that requires more than routine maintenance. The checklist should be used to conduct a visual-based field evaluation to further refine the preliminary analysis.
The rooftop unit inventory spreadsheet can be used to gather basic RTU information, such as number, size, age, and general condition. The detailed fields in the spreadsheet can be used to gather additional information, such as controls, usage patterns, and features for additional analysis of the RTUs identified for retrofit, replacement, or further analysis.
The rooftop unit (RTU) decision tree can be used for preliminary screening for replacement of RTU units with more efficient units. This decision tree organizes RTUs into bins for “retrofit,” “replacement,” “no action,” or “needs further analysis.”
This report summarizes an evaluation of LED recessed downlight luminaires in the guest rooms at the Hilton Columbus Downtown hotel in Columbus, OH. The facility opened in October of 2012, and the U.S. Department of Energy (DOE) conducted a post-occupancy assessment of the facility in January–March of 2014. Each of the 484 guest rooms uses seven 15 W LED downlights: four downlights in the entry and bedroom and three downlights in the bathroom. The 48 suites use the seven 15 W LED downlights and additional fixtures depending on the space requirements, so that in total the facility has more than 3,700 LED downlights. The downlights are controlled through wall-mounted switches and dimmers. A ceiling-mounted wireless vacancy sensor ensures that the bathroom luminaires are turned off when the room is not occupied.