A case study of the overview, process, and results of the re-tuning that was conducted in a building in Arlington, Virginia by Vornado Realty Trust in October 2012. Re-tuning provided the facilities management team with the ability to identify and understand building scheduling opportunities that drove significant, low-cost energy savings. Five measures were conducted, many of which pertained to the HVAC system.
Advanced SearchYour search resulted in 21 resources
This dynamic document provides background information to any potential audience of building re-tuning training. This document provides background information specifically geared toward small- to medium-sized commercial building operations. It introduces basic building energy terminology associated with building energy use to “prime” targeted participants to get the most out of the building re-tuning training. The intent is for participants who are less familiar with the concepts to review this material before taking the building re-tuning training class.
The primary audience for this instructor manual is the person who will be teaching the re-tuning course. In addition, community college instructors, retro-commissioning training providers and building operator training providers may find value in the material presented in this instructor manual as well. The purpose of this course is to help building operations staff to learn how to operate buildings more efficiently, reduce operating cost and provide energy savings. The knowledge and skills learned through the training will be highly valued by organizations and companies seeking to improve the performance of
Tower Companies, a DC based owner of large multi-tenant buildings and Better Buildings Challenge partner, engaged in an aggressive program to take measured data from their buildings and turn it into real energy savings. This case study, completed by Tower in partnership with the National Resources Defense Council (NRDC) describes outcomes at three properties. The case study was highlighted on a Better Buildings Webinar on February 5, 2014.
Case study describing how adidas implemented a best practice of a planned replacement program for its rooftop units (RTUs), which resulted in significant cost and energy savings. The case study outlines the planning process, implementation, results, and the future plans of their RTU replacement program.
Appendices for the ENERGY STAR® Action Workbook for Congregations. Appendices were developed after reviewing results of energy audits of churches and identifying best savings opportunities. These opportunities are converted into actionable worksheets specifically geared to congregations and worship facilities.
This case study details the very successful Walgreens proactive RTU replacement program that has resulted in 50% efficiency improvements. The streamlined process allows Walgreens to reduce installed cooling capacity, increase RTU efficiency, provide improved service, and reduce overall costs compared to emergency replacements.
JCPenney saved over 47 million kWh and $5 million with variable frequency drive retrofits of rooftop units across 131 stores. The case study describes the decision process and results of this successful program.
The case study details how the U.S. Navy saved over 100 MWh annually with five year payback by installing advanced RTU control retrofit packages at Pearl Harbor, Hawaii.
In FY14, BTO funded PNNL to develop and integrate AFDD methods for both air-side and refrigerant-side fault detection and diagnostics with one of the leading advanced RTU controllers sold in the market today. The work also includes testing and validating the integrated solution in the field. If the results from the field demonstrations show reliable fault diagnostics, it will encourage utilities to provide incentives to pursue the integrated technology because it makes the retrofit controller more cost effective and could make market adoption of the retrofit controller even more attractive to building owners.
Seven AFDD algorithms were developed, deployed and tested on the RTU controller for detecting and diagnosing faults with RTU economizer and ventilation operations using sensors that are commonly installed for advanced control purposes.