Sinisa Novakovic, owner of Mishka’s café in downtown Davis, had two goals for the recent lighting upgrade in his café: create a cozy, inviting atmosphere for customers and save energy. In the main seating area alone he was able to cut his lighting energy use 85% by upgrading to LED lighting. Throughout the rest of the café, energy consumption for lighting has been cut in half, reducing Mishka’s annual energy use by over 10,000 kWh and saving Novakovic nearly $2,000 every year in energy costs. The lighting upgrade will have paid for itself after just eight months.
Advanced SearchYour search resulted in 17 resources
The California Energy Commission’s Public Interest Energy Research (PIER) program sponsored development of bi-level parking garage luminaires for the University of California, Davis that integrate intelligent controls with bi-level electronic drivers or ballasts to control light output based on garage occupancy. Luminaires operate at a reduced level during vacancy and switch to full light output upon occupancy. Many of the products may be combined with traditional photocontrols to maximize energy savings.
Energy savings can be achieved in corridors and other secondary spaces with an occupancy-based adaptive lighting system. Such a system is generally composed of occupancy sensors, dimmable ballasts and a communication platform. The system automatically lowers light levels to the minimum footcandles required by safety codes during vacancy and raises light output to the recommended level for occupant comfort during occupied periods. The adaptive lighting system installed at the Latham Square office building is based on Lutron’s Energi TriPak solution, a stand-alone platform for adaptive lighting that employs cost-effective wireless control devices and programmable dimming ballasts.
Adaptive exterior lighting is a relatively new concept recognized by the lighting industry and energy regulators as a potential method to increase energy savings in outdoor applications. Many adaptive exterior lighting products are being developed and have been introduced into the marketplace, allowing users to implement dynamic lighting designs that offer 30%–75% energy savings over traditional systems. These savings are achieved by coupling advanced lighting controls with an efficacious, dimmable source.
In the summer of 2010 the California Lighting Technology Center (CLTC) and Philips Hadco produced a bi-level solution that combined a dimmable LED source and a mounting collar equipped with occupancy sensors. The collar provides 360-degree occupancy sensor coverage. This demonstration involved whole-head replacement of the existing luminaires, but results could also be achieved with a retrofit kit. The new luminaires feature good color quality, improved efficiency and a longer lifespan. Adaptive controls enable the bi-level luminaires to reduce power to 50% during vacant periods and increase to 100% light output when occupants approach. Switching between the two light levels maintains adequate light for security and wayfinding while maximizing energy savings.
In 2012, University of California Davis upgraded its exterior lighting as part of the university’s Smart Lighting Initiative. Wall packs on campus, like other exterior lighting fixtures, were retrofitted with dimmable LED sources, motion sensors, and wireless controls. This allowed the units to be incorporated into an adaptive campus-wide lighting control system. The system offers an intelligent, networked approach to lighting and energy management with improved lighting quality and optimal energy efficiency.
The objective of this demonstration project was to evaluate market-ready retrofit technologies for reducing the energy and water use of multi-load washers in healthcare and hospitality facilities. Specifically, this project evaluated ozone laundry technology in both the healthcare and hospitality sectors. This report documents the demonstration of ozone laundry system installations at the Charleston Place Hotel in Charleston, Sout Carolina, and the Rogerson House assisted living facility in Boston, Massachusetts.
Case study on how CKE, in collaboration with Southern California Edison’s (SCE) New Products Development and Launch (NPDL) organization, field tested an advanced demand defrost control system for walk-in coolers and freezers in their Carl’s Jr. restaurants.
To maximize the respective benefits of open- and closed-loop systems, and minimize their limitations, the California Lighting Technology Center (CLTC) developed a dual-loop photosensor control system for skylight applications. The system features a control algorithm that monitors the open- and closed-loop photosensors and controls the electric light to provide the designed light level. It also automatically recalibrates nightly to adjust to long-term changes to the interior space. Results show the dual-loop technology delivers more consistent lighting and greater energy savings.
The Integrated Classroom Lighting System (ICLS) delivers flexible, high-quality, energy-efficient lighting that is easy to use and maintain. ICLS system retrofits can either use existing fixture housings, only replacing lamps and ballasts, or the fixtures can be entirely replaced with a one-to-one retrofit. ICLS fixture controls, with features such as scene control, dimming, daylight harvesting, and occupancy sensing, automatically maximize energy savings while giving teachers optimal control of their classroom lighting.